This catalogue describes RO SERIES COOLERS made of copper and steel.
Each data sheet provides the technical information about the heat exchanger used for cooling oil hydraulic system and about fans operated by electric or hydraulic motor.
Please contact IRA for aggressive ambient
The heat exchanger should be installed in such a way that there should be no obstacles to the air flow, respecting the minimum distance from the wall (1/2 fan diameter) so as to ensure a natural flow of cooling air. The cooler can be fitted in vertical and horizontal position. RO series coolers are normally used for cooling hydraulic circuits and installed on the return lines: they must be protected from impact and mechanical vibrations by support and must be connected to the circuit with flexible pipes. To prevent any damage caused by changes in flow, hammering and pulsations we recommend installing a by-pass valve.
- mineral oil
For other fluid consuls IRA RADIATORI
Cleaning oil side
After having dismantled the exchanger, carry out the cleaning procedure by circulating de-greasing substance inside the radiator compatible with steel. Wash with hydraulic oil before reconnecting the cooler.
Cleaning air side
Carry out this procedure using compressed air. Make sure that the direction of the jet is parallel to the fins so that they are not damaged. If the blockage of the exchanger is caused by build up of oil or grease, c1eaning can be carried out using a jet of steam or hot water. During c1eaning procedures the electric motor must be adequately protected.
During operation of heat exchangers observe following instructions:
- Do not remove the fan grilles
- Electrical connections must be made by skilled electricians in accordance with the attached electrical diagrams
- Exterior surfaces of heat exchangers may reach high temperatures so adequate guards must be installed or the unit must be mounted in an inaccessible position
- Do not perform work on the hydraulic motor until the hydraulic pipelines have been disconnected